The Integrator is a custom device that RAB programs for each customer
Custom programming ensures proper integration with all BACnet applications
Integrator: The Integrator is a BACnet compliant device and provides the required protocol to communicate with the BACnet workstation. The Integrator communicates with the Lightcloud Gateway to allow Lightcloud to interact with building management systems.
The BACnet workstation is capable of displaying the status of, or setting the state of, all BACnet compliant devices connected to the network. Communication between the Lightcloud Gateway and the BACnet workstation is through the Integrator. The Integrator maintains internal memory regions for the Lightcloud Gateway to write individual device status and regions where commands initiated from the BACnet workstation are held for the Lightcloud Gateway. The memory area used for status, commands, device names or device grouping is defined in a configuration file. The configuration file is formatted as a CSV (Comma Separated Value) file. This file is unique to every installation and changes when a device is added or removed.
BACnet Testing Labs (BTL): B-ASC Ver. 12
LonMark 3.4 Certified: ProtoNode Series
TUV Approved: UL 916 EN 60950-1 EN 50491-3 and CSA C22-2 standards
DNP 3.0 Conformance Tested:
CE & FCC Approved:
Power: 9-30 VDC or 12-24 VAC (RS-422 = 15-30 VDC or 12-24 VAC)
Current Draw: FPC-N34 @ 12V = 240 mA FPC-N35 @ 12V = 250 mA
M-Bus: Slave: 500 mA @12V Master (1 Slave): 580 mA @ 12V Master (64 Slave): 980 mA @ 12V
BACnet Support: Alarm & Event notification read properties multiples BACnet COV's, Trend Logging, BBMD and optional BACnet Router support. Support up to 10,000 BACnet Objects DIP switches are for setting MAC Address, Node-ID, Baud Rate on the RS-485 Field protocol